Give the specific 2002 NEC references related to any violations you find. Write Joe a Violation Notice rather than sending in a copy of the Code rule. Send your response, in 25 words or more, to Joe Tedesco at 350 North St., Boston, MA 02113 or [email protected]. Please include your company name, job title, address, phone number, Social Security number and e-mail address. Previous winners are not eligible. Winners will be awarded $75 in the case of one winner, $50 each for two winners and $25 each for three winners.
Hint: Thisarea is being used as an automobile spray booth.
James Myrick, an electrician with Myrick and Sons Electrical Contractors, Graham, N.C., provided the following answer.
The liquidtight flexible metal conduit is not properly secured according to 350.30(A).
The front working-space depth does not comply with Table 110.26(A)(1).
Class 2 thermostat wire installed in the same raceway with the power supply violates Section 300.3 (C)(1). FPN: See 725.55(A) for Class 2 and Class 3 circuit conductors.
Attention CEE News readers. Do you have a photo of a glaring Code violation?
E-mail your digital photos and descriptions to [email protected] or mail them to 350 North St., Boston, MA 02113. Your photo may be published in our upcoming photo gallery of America's worst NEC violations.