Any ungrounded conductors that supply, or pass through, a structure must have a means of being disconnected [225.31]. But where do you put the disconnecting means?
It must be:
1. Inside or (immediately) outside the structure being served [225.32].
2. At a readily accessible location near the point where the conductors enter the structure.
Four exceptions apply to the rules just stated. The disconnect