When replacing a nongrounding receptacle with a grounding-type receptacle, you can connect the equipment grounding conductor of a grounding-type receptacle or branch circuit extension to any of six places [250.130(C)]. Those are:
1) Any accessible point on the grounding system as described in Sec. 250.30.
2) Any accessible point on the grounding electrode conductor.
3) The equipment gro