Q. What is the minimum size requirement for branch circuit overcurrent protection?
Find the Answer
A. Branch-circuit overcurrent devices must have a rating of not less than 125% of the continuous loads, plus 100% of the noncontinuous loads [210.20(A)]. Note: See Sec. 210.19(A)(1) for branch-circuit conductor sizing requirements.
Exception: If the assembly and the overcurrent devices are both liste