Q. How do you determine the minimum number of general lighting and general-use branch circuits required by the NEC for dwellings?
Find the Answer
A. The minimum number of general lighting and general-use receptacle branch circuits must be determined by dividing the total calculated load in amperes by the ampere rating of the circuits used [210.11(A)].
For example, let’s say you’re trying to determine how many 15A, 120V ci