Q. Does the NEC require GFCI protection when replacing a non-GFCI receptacle in an existing building?
Find the Answer
A. When existing receptacles are replaced in locations where GFCI protection is currently required, the replacement receptacles must be GFCI protected [406.4(D)(3)].
Exception: Where receptacle replacement is impracticable, such as where the outlet box size won’t permit the installation of