Q. Where is GFCI protection required for 15A and 20A, 125V rated receptacles in locations other than dwelling units?
Find the Answer
A. GFCI protection is required for 15A and 20A, 125V receptacles installed in the following commercial/industrial locations [210.8(B)]:
1) Bathrooms. 15A and 20A, 125V receptacles installed in commercial or industrial bathrooms must be GFCI protected. See the definition of “