Q. Where does the Code require overcurrent protection to be located in a circuit?
Find the Answer
A. Except as permitted by Sec. 240.21(A) through (H), overcurrent devices must be placed at the point where the branch-circuit or feeder conductors receive their power. Taps and transformer secondary conductors aren’t permitted to supply another conductor (tapping a tap isn’t permitted).