Q. What is the Code requirement for protecting a motor from short circuit, ground fault, and overload with a single device?
Find the Answer
A. A motor can be protected against overload as well as short circuit and ground fault by a single overcurrent device sized to the overload requirements contained in Sec. 430.32 [430.55].
For example, let’s say you have a 5-hp, 230V, single-phase motor with a service factor of 1.15 an