Q. What are the rules for sizing a supply side bonding jumper for parallel raceways?
Find the Answer
A. If the ungrounded supply conductors are paralleled in two or more raceways or cables, you must size the supply-side bonding jumper for each raceway or cable in accordance with Table 250.102(C)(1), based on the size of the largest ungrounded conductor in each raceway or cable [Sec. 250.102(C)(2)].