Q. What is the Code rule for sizing conductors serving a single continuous duty motor?
Find the Answer
A. Conductors to a single motor must be sized not less than 125% of the motor full load current (FLC) rating as listed in Table 430.247 [Direct-Current Motors], Table 430.248 [Single-Phase Motors], or Table 430.250 [Three-Phase Motors (430.22)].
Let’s run through an example problem to show you exactly how to choose