Q. What are the rules for sizing an equipment bonding jumper sized for parallel feeder circuits in a cable?
Find the Answer
A. Bonding jumpers on the load side of feeder and branch circuit overcurrent devices are sized in accordance with Sec. 250.122, based on the rating of the circuit overcurrent device [250.102(D)]. For example, let’s say you’re installing parallel cables that are protected by a 1,200A overcurrent device. A