All questions and answers are based on the 2014 NEC.
Q. What are the requirements for a building service disconnecting means?
A. The service disconnecting means must open all service-entrance conductors from the building premises wiring [230.70]. It must be placed at a readily accessible location either outside the building or inside nearest the point of service conductor entry [230.70(A)(1)] (Fig. 1).