All questions and answers are based on the 2011 NEC.
Q. What is the Code rule for sizing feeder conductors, both ungrounded and neutral? Please show an example.
A. Section 215.2(A)(1) requires that the minimum feeder conductor ampacity, before the application of ambient temperature correction [310.15(B)(2)(a)], conductor bundling adjustment [310.15(B)(3)(a)], or both, must be no less than 125% of the continuous load, plus 100% o