Q. Can I pull Type NM cable in a PVC sleeve located in a ground floor slab for the kitchen counter island?
A. No. Type NM cable must not be used in wet or damp locations [334.12(B)(4)].
The interior of enclosures or raceways installed in an underground installation are considered to be a wet location [300.5(B)]. Cables and insulated conductors installed in underground enclosures or raceways must be listed for u