In which area of a dwelling unit are both GFCI and AFCI protection required?
A. No area. It is not possible to provide both for a receptacle outlet.
C. Kitchen and laundry areas
D. Dishwasher located in a kitchen
Find the Answer
A change in the 2014 NEC now requires both AFCI and GFCI protection for the 15A and 20A outlets in kitchen and laundry areas [see Sec. 210.8(A) and Sec. 210.12(A)].