In this episode, Russ shows us a cable support violation. As noted in Sec. 320.30(B) and Sec. 334.30, Type NM and Type AC cables shall be supported within 12 in. of the enclosure and then every 4.5 ft thereafter.
In this episode, Russ finds another violation of the dedicated space requirements outlined in Sec. 110.26(E) of the NEC. The steam pipes running directly over the top of this panelboard need to be relocated, or the panelboard needs to be moved.