In this episode, Russ shows us a violation of Sec. 314.28(A)(1) in the 2017 NEC. When using a metal wireway as a pull box, the spacing between the raceway entries needs to be eight times larger than the largest raceway. For the 4-in. conduit this means 32 in. of space. However, the metal wireway is only about 6 in. wide.