Q. Is a disconnect required to be within sight of electric space-heating equipment if the unit has a factory-installed circuit breaker?
A. No. A unit switch with a marked “off” position that is an integral part of the equipment can serve as the heater disconnecting means, if it disconnects all ungrounded conductors of the circuit [424.19(C)].