In the latest installment of Moving Violations, Russ looks at a row of receptacles on posts. Many of these receptacles have been smashed and now have exposed wires or broken parts that violate Sec. 110.12(B).
It seems that these receptacles have been damaged by vehicles backing into the parking spaces in front of the poles. Section 110.27(B) says that, in locations where electrical equipment may be exposed to physical damage, some type of enclosures or guards need to be installed to prevent damage.