In this episode, Russ finds a whole collection of Code violations in an installation intended to provide light off the corner of a building, and surmises the installer was in a hurry. He found luminaires supported by nothing but electrical metallic tubing (EMT), a violation of Sec. 358.12(2), and a run of conduit down the wall that's entirely lacking clips or other fasteners for support, a violation of Sec. 358.30. What other violations can you identify here?